If the Gas Vent is required to be supported where it penetrates the floor/ceiling Support Plates should be applied. These square heavy gauge galvanised plates must be fixed through the corner holes on top of the floor joist or slab through which the chimney is passing. The flanged collar is clamped to the vent so that the lower flange rests on the support plate. A Firestop Spacer must be used on the underside of the opening at ceiling level. The MAXIMUM height that can be supported, including any suspended lengths, is 18m (60ft). The combination of lengths and fittings used should be such that no joint occurs within the floor space.
Gas Vent lengths and fittings are available with the outer casing fabricated from galvanised steel. The flue liner is aluminium. Vertical seams are rolled and securely locked. The inner and outer casing are joined at one end only and a 6mm (1/4") air gap is incorporated: the inner liner is thus free to expand as the temperature changes in the vent.